Wenzhou Korlen Electric Appliances Co., Ltd.
Model No.: KNL1-100
Breaking Capacity: Low Voltage Circuit Breakers
Operation: Manual Type
Speed: Normal Type Circuit Breaker
Arc-extinguishing Medium: Air
Poles Number: 2
Type: Circuit Breaker
Function: Conventional Circuit Breaker
Certification: CB, CE
Rated Limiting Short-circuit Current: 3000A
Rated Worling Current: 16;20;25;32;40;50;63A
Rated Working Voltage: 240V/415V
Place of Origin: Wenzhou; Zhejiang; China
HS Code: 8536200000
KNL1RCCB is in conformity with the standard of IEC61008.The RCCB can cut off the fault circuit immediately on the occasion of shock hazard or earth leakage of trunk,thus,it's suitable to avoid the shock hazard and fire caused by earth leakage.The RCCB is mainly suitable for use in varieties of plants and enterprises,building.
How to check your Circuit Breaker?
1.if your power goes off because your circuit breaker has tripped,look for the lever in the "off" position(A) or where the button has popped out(B).
2.Switch off lights and unplug all appliances on the faulty circuit.
3.Push the operating lever to the "on" position(A) .or push in the button on the circuit breaker(B).
4.If the circuit breaker continues to trip,call a licensed electrician.
|Rated working voltage||240/415V|
|Rated working current||63,80,100A|
|Rated residual operating current||0.03,0.1,0.3,0.5A|
|Rated residual un-operating current||0.015,0.05,0.15,0.25A|
|Sensibility||AC Type,A Type,S Type|
|Maximum operating time||IΔn t≤0.1s , 5IΔn t≤0.04|
|Rated making and breaking capacity||1500A|
|Limiting value of un-operating current||6In|
|Rated limiting short-circuit current||3000A|